NSW Fair Trading has negotiated with the Infinity Cable Co Pty Ltd for the recall of three batches of *Infinity* brand insulated electrical cables. The cables are Thermoplastic Sheathed electric cable - commonly known as TPS.
The specific cable is 2.5mm "Polymeric Insulated Electrical Cable which is PVC Sheathed, PVC Insulated, Flat and Flexible Low Voltage Electrical Cable" also commonly known as "TPS 2.5mm Twin and Earth" (ThermoPlastic Sheathed Electrical Cable, active, neutral and earth). The batch numbers being recalled are INFH 190311, INFH 210912 and INFMEL 081112.
The cables that are the subject of the recall have been subjected to laboratory testing commissioned by NSW Fair Trading and conducted by TUV Rheinland in Victoria. The sample submitted for testing by NSW Fair Trading failed the commissioned tests against AS/NZ 5000.2:2006 and relevant parts of AS/NZ 3808. The testing failure indicates that the plastic coating insulation on the cable can become brittle when exposed to high temperatures over time whether through exposure to heat generated by the copper wire itself or through exposure to external heat such as if it is used in the roof of homes in warmer parts of NSW.
Information provided to Fair Trading is that the product has been stocked in NSW for about one year. NSW Fair Trading has been in contact with electrical safety regulators around Australia and advised them of the concerns regarding this cable. NSW Fair Trading believes that the cable may also be sold in other States and Territories. Fair Trading has no information that any incidents or injuries to people or property has resulted from the cable. However, given the cable batches have failed essential safety tests the recall is needed to prevent possible future problems.
The company is publishing recall notices in newspapers and writing to everyone they have sold the cable to requesting them to return the recalled batches of cable to the place of sale.The company has agreed to provide information to Fair Trading concerning the importation and sale of the recalled batches of cable and to provide ongoing reports to Fair Trading of the recall and disposal of the affected cables.
Fair Trading will be issuing a media release regarding the recall in addition to the company*s own recall notices. Our advice will of course be that consumers should not try to inspect the cable and that any work on wiring or cable should only be done by licensed electricians. We will also recommend to consumers that if they have recently had building work done, or wiring changed or installed, they should contact the responsible builder or electrician for advice on whether the recalled cable was used. If it was, we will recommend that they talk to the builder or electrician about getting the cable inspected and replaced.
It would be appreciated if you could make your members and stakeholders aware of this recall through your own communication channels and networks. The formal information that you could direct people towards will be on the Fair Trading website www.fairtrading.nsw.gov.au.